ARTICLE 3. SEWERS
Unless the context clearly indicates otherwise, the meaning of words and terms as used in this article shall be as follows:
(a) Building Drain shall mean that part of the lowest horizontal piping of a drainage system which receives the discharge from soil, waste, and other drainage pipes inside the walls of the building and conveys it to the building sewer, beginning five feet outside the innerface of the building wall.
(b) Building Sewer shall mean the extension from the building drain to the public sewer or other place of disposal.
(c) B.O.D. (denoting Biochemcial Oxygen Demand) shall mean the quantity of oxygen utilized in the biochemical oxidation of organic matter under standard laboratory procedure in five days at 20 degrees centigrade, expressed in parts per million by weight.
(d) pH shall mean the logarithm of the reciprocal of the weight of hydrogen ions in grams per liter of solution.
(e) Individual Domestic means any single family residence, commercial business, office, institution, school, church or public entity having an individual direct or indirect connection to the wastewater facilities of the city and on individual city or private water service meter, or connection to any such water service.
(f) Industrial means any industrial business engaged in the manufacturing or processing of one or more products, and in which wastewaters are produced from such manufacturing or processing and said wastewaters are discharged directly or indirectly to the wastewater facilities of the city.
(g) Multi-domestic means any multi-family residence, apartment or mobile home and any commercial business, office, institution, school, church or public entity having a direct or indirect connection to the wastewater facilities of the city and not having an individual water service meter but is served with city or private metered water by the owner of the property on which it is located,
(h) Superintendent shall mean the superintendent of the city or his or her authorized deputy, agent or representative.
(i) Sewage shall mean a combination of the water-carried wastes from residences, business buildings, institutions and industrial establishments, together with such ground, surface, and storm waters as may be present.
(j) Sewer shall mean a pipe or conduit for carrying sewage.
(k) Public Sewer shall mean a sewer in which all owners of abutting properties have equal rights, and is controlled by public authority.
(l) Combined Sewers shall mean sewers receiving both surface runoff and sewage, are not permitted.
(m) Sanitary Sewer shall mean a sewer which carries sewage and to which storm, surfaces and groundwaters are not intentionally admitted,
(n) Storm Sewer or Storm Drain shall mean a sewer which carries storm and surface waters and drainage, but excludes sewage and polluted industrial wastes,
(o) Sewage Treatment Plant shall mean any arrangement of devices and structures used for treating sewage.
(p) Suspended Solids shall mean solids that either float on the surface of, or are in suspension in water, sewage, or other liquids, and which are removable by laboratory filtering.
(q) User means any person as defined in section 1-102, including an institution, governmental agency or political subdivision producing waste water requiring processing and treatment to remove pollutants and having premises connected to the wastewater facilities,
(r) Wastewater means sewage, the combination of liquids and water carried wastes from residences, commercial and industrial buildings, institutions, governmental agencies, together with any ground, surface or storm water that may be present.
(s) Normal wastewater. The strength of normal wastewater shall be considered within the following ranges:
(1) A five day biochemical oxygen demand of 300 milligrams per liter or less;
(2) A suspended solid concentration of 350 milligrams or less;
(3) Hydrogen ion concentration of 5.0 to 9.0.
The owner of all houses, buildings, or properties used for human occupancy, employment, recreation, or other purposes, situated within the city and abutting any street, alley, or right-of-way in which there is located a public sanitary sewer of the city is hereby required at his or her expense to install suitable toilet facilities therein, and to connect such facilities directly to the public sewer in accordance with the provisions of this article, within 90 days of official notice to do so, providing that said public sewer is within 140 feet of the property line.
(a) No person shall uncover, make any connections with or opening into, use, alter, or disturb any public sewer or appurtenance thereof without first obtaining a written permit from the city. There shall be charged a fee as set forth in the city’s fee resolution for such permit at the time of making application.
(Code 1991; Ord. 2000-6, Sec. 2; Code 2010)
Any person desiring to make a connection to the city sewer system shall apply in writing to the city clerk who shall forward the application to the utility superintendent. The application shall contain:
(a) The legal description of the property to be connected;
(b) The name and address of the owner or owners of the property;
(c) The kind of property to be connected (residential, commercial or industrial);
(d) The point of proposed connection to the city sewer line.
All costs and expense incident to the installation and connection of the building sewer shall be paid by the owner. The owner shall indemnify the city from any loss or damage that may directly or indirectly be occasioned by the installation of the building sewer.
The connection of the building sewer into the public sewer shall be made at the “Y” branch if such branch is available at a suitable location. Where no properly located “Y” branch is available, the connection shall be made in the manner approved by the maintenance superintendent and at a location designated by the superintendent.
A separate and independent building sewer shall be provided for every building except where one building stands at the rear of another on an interior lot and no private sewer is available or can be feasibly constructed to the rear building. In such case, the building sewer from the front building may be extended to the rear building and the whole considered as one building sewer.
The building sewer shall be constructed of ductile iron pipe, or approved equal; or an approved PVC pipe, as described in the City of Benton Design Standards and Standard Construction Specifications for sanitary sewer projects. Any PVC pipe to be installed on any building sewer shall not be approved by the city until the owner has furnished descriptive literature and typical sample section of the plastic pipe proposed for installation, to the city for inspection and review. All joints on all pipe installed shall be tight and waterproof. Any part of the building sewer that is located within 10 feet of a water service pipe or city water main shall be constructed of approved ductile iron soil pipe with approved joints. No building sewer shall be installed within three feet of existing gas lines. If installed in filled or unstable ground, the building sewer shall be constructed of ductile iron soil pipe, except that non-metallic material may be accepted if laid on a suitable concrete bed or cradle as approved by the city.
The size and slope of the building sewer to be installed shall be subject to the approval of the city inspector, but in no event shall the diameter of the pipe be less than four inches. The slope at which a six inch pipe is to be laid shall be not less than 1/8 inch per foot and for four inch pipe, not less than 1/4 inch per foot. Any grades for the pipe, which are proposed for installation at grades less than these specified, shall be approved by the city inspector prior to placement.
Whenever possible the building sewer shall be brought to the building at an elevation below the basement floor. No building sewer shall be laid parallel to or within three feet of any bearing wall, which might thereby be weakened. The depth shall be sufficient to afford protection from frost. The building sewer shall be laid at a uniform grade and in straight alignment insofar as possible. Changes in direction shall be made only with approved curved pipe and fittings, including cleanout fittings.
At buildings in which the building drain is too low to permit gravity flow to the public sewer, sanitary sewage carried by such drain shall be lifted by approved artificial means and discharged to the building sewer. The use of any pumping equipment for which cross-connections with a public water supply system are needed, is prohibited. The total costs of pumping equipment and pumping equipment operational costs shall be those of the owner.
No building sewer shall be laid across a cesspool, septic tank or vault until the cesspool, septic tank or vault has been well cleaned and filled with an approved earth or sand fill, then thoroughly tamped and water settled. Cast iron pipe may be used across cesspools or septic tanks, if proper bedding and support for the sewer pipe is acquired.
All excavation required for the installation of the building sewer shall be open trench work unless otherwise approved by the city. Pipe laying and backfill shall be performed in accordance with ASTM specifications C12-19, except that no backfill shall be placed until the work has been inspected and approved.
All joints in the building sewers shall be made watertight. If recommended by the city inspector, a water pressure test shall be made on the completed sewer to insure a compliance with this requirement, requiring that the building sewer withstand an internal water pressure of 5 psi., without leakage.
Cast iron pipe with lead joints shall be firmly packed with oakum or hemp and filled with molten lead, Federal Specifications QQ-L-156, not less than one inch deep. Lead shall be run in one pour and caulked and packed tight. No paint, varnish or other coatings shall be permitted on the jointing material until after the joint has been tested and approved.
Joints for all plastic pipe used in building sewers shall be the slip type joints or solvent weld type, approved by the city.
Joints between any two different types of pipes shall be made with lead, asphaltic jointing materials or concrete, as approved by the city. All joints shall be watertight and constructed to insure minimum root penetration and to the satisfaction of the city.
All excavations for buildings sewers shall be adequately guarded with barricades and lights so as to protect the public from hazard. Streets, curb and gutters, sidewalks, parkways and other public property removed or damaged during the installation of the building sewer, shall be repaired or replaced in a manner acceptable to the city and at the total expense of the owner. It is further agreed that any parties involved in any excavating or installation work for sewer installations as above set out, will hold the city harmless from any and all damages to persons or property resulting from or growing out of any opening or excavation or any negligent act or from any operation made within the city.
(a) If any person as defined in section 1-102 shall fail to connect any dwelling or building with the sewer system after being noticed, the city may cause such buildings to be connected with the sewer system as authorized by K.S.A. 12-631.
(b) The cost and expense, including inspection fees, shall be assessed against the property. Until such assessments shall have been collected and paid to the city, the cost of making such connection may be paid from the general fund or through the issuance of no fund warrants.
It shall be unlawful to construct or maintain any privy, privy vault, septic tank, cesspool, or other facility intended or used for the disposal of sewage except as provided in this article.
Where a public sanitary sewer is not available under the provisions of section 15-302 the building sewer shall be connected to a private sewage disposal system complying with the provisions of sections 15-311 to 15-316.
Before commencing construction of a private sewage disposal system, the owner shall first obtain a written permit signed by the building inspector and the maintenance superintendent. The application shall be accompanied by any plans, specifications or other information deemed necessary by the building inspector and maintenance superintendent. A permit and inspection fee pursuant to the building code shall be paid to the city at the time the application is filed.
The maintenance superintendent or his or her authorized representative shall be allowed to inspect the work at any stage of construction and the applicant shall notify the superintendent when the work is ready for final inspection or before any underground portions are covered. The inspection shall be made within 48 hours of the receipt of notice by the superintendent.
(a) The type, capacities, location, and layout of the private sewage disposal system shall comply with all recommendations and requirements of the Water Pollution Control Section of the Kansas State Department of Health. No permit shall be issued for any private sewage disposal system employing subsurface soil absorption facilities where the area of the lot is less than one acre. No septic tank or cesspool shall be permitted to discharge to any public sewer or natural outlet.
(b) At such time as a public sewer becomes available to a property served by a private sewage disposal system, as provided in section 15-302, a direct connection shall be made to the public sewer in compliance with this article, and any septic tank, cesspool, and similar private sewage disposal facilities shall be abandoned and filled with suitable and acceptable materials.
No statement contained in this article shall be construed to interfere with any additional requirements that may be imposed by the city or county health officer.
It shall be unlawful for any person to deposit or discharge from any source whatsoever any sewage or human excrement upon any public or private grounds within the city, or to permit the contents of any privy vault or septic tank to be deposited or discharged upon the surface of any grounds. Any unauthorized or unapproved privy vault, septic tank or other means or places for the disposal of sewage, excrement and polluted water may be abated as a public nuisance upon the order of the city or county board of health in accordance with the laws of Kansas.
(K.S.A. 12-1617e; 12-1617g; Code 1991)
It shall be unlawful for any unauthorized person to maliciously, willfully, or negligently break, damage, destroy, uncover, deface or tamper with any sewer, structure, appurtenance, or equipment which is part of the municipal sewer system.
It shall be unlawful to discharge to any natural outlet within the city or in any area under the jurisdiction of the city any sanitary sewage, industrial wastes or other polluted waters except where suitable treatment has been provided in accordance with the provisions of this article.
The size, slope, alignment, materials, excavation, placing of pipe, jointing, testing and backfilling shall all conform to the requirements of the building and plumbing codes or other applicable rules, regulations and standards of the city.
Old building sewers may be used in connection with new buildings only when they are found, on examination and test by the maintenance superintendent, to meet all requirements of this article.
All garages, filling stations, milk plants or other commercial or industrial plants connected to the public sewer shall construct and maintain proper and sufficient interceptors or traps to prevent the discharge of any sand, mud, sediment, litter, waste or any substance harmful to the effective operation and maintenance of the city sewer system, into the building sewer.
(a) It shall, be unlawful to connect downspouts from any roof area, drains from any building foundation, paved areas, yards or open courts, or, to discharge liquid wastes from any air conditioning unit or cooling device having a capacity in excess of one ton per hour or one horsepower into any city sanitary sewer.
(b) All discharges prohibited in subsection (a) may be discharged into the public gutter or storm drains or open drainage ditches provided such discharge does not create a nuisance. No such liquids may be discharged into any unpaved street or alley.
Discharges from air conditioning units in excess of one ton per hour or one horsepower may be permitted into a building sewer upon approval of the utility superintendent where there is a finding that such cooling water cannot be recirculated and that such waste water does not overload the capacity of the sewer or interfere with the effective operation of the sewage disposal works of the city.
No person shall discharge any of the following waters or wastes to any public sewer:
(a) Liquid or vapor having a temperature higher than 150 degrees Fahrenheit;
(b) Water or waste which may contain more than 100 parts per million, by weight, of fat, oil or grease;
(c) Gasoline, benzene, naphtha, fuel oil, or other flammable or explosive liquid, solid or gas;
(d) Garbage that has not been properly shredded;
(e) Ashes, cinders, sand, mud, straw, shavings, metal, glass, rags, feathers, tar, plastics, wood, paunch manure, or any other solid or viscous substance capable of causing obstruction to the flow in sewers or other interference with the proper operation of the sewage works;
(f) Waters or wastes having a ph lower than 5.5 or higher than 9.0 or having any other corrosive property capable of causing damage or hazard to structures, equipment and personnel of the sewage works;
(g) Waters or wastes containing a toxic poisonous substance in sufficient quantity to injury or interfere with any sewage treatment process, constitute a hazard to humans or animals, or create any hazard in the receiving waters of the sewage treatment plant;
(h) Water or wastes containing suspended solids of such character and quantity that unusual attention or expense is required to handle such materials at the sewage treatment plant;
(i) Noxious or malodorous gas or substance capable of creating a public nuisance.
(a) Bills shall be rendered monthly as provided in section 15-224 and shall be collected as a combined utility bill.
(b) Any person at the time of beginning or terminating service who receives service for a period of less than 17 consecutive days shall be billed at no less than one-half of the regular minimum monthly rate. For service of 17 consecutive days or more the charge shall be not less than full regular minimum monthly rate.
(a) In the event any person, except the United States and the state of Kansas or any political subdivision thereof, shall fail to pay the user charges when due, water service shall be terminated as provided in sections 15-102:104.
(b) In lieu of terminating water service, the governing body may elect to assess such delinquent charges as a lien upon the real estate serviced as provided in section 15-106, and the city clerk shall certify such delinquent charges to the county clerk to be placed on the tax roll and collected in like manner as other taxes are collected.
There is levied on such sewerage system user having any sewer connection with the sewerage system of the city or otherwise discharging sewage, industrial waste, or other liquids, either directly or indirectly into the city's sewerage system which ultimately enters the sewerage system, a sewerage charge. Subject to the exceptions provided in this chapter, such charges shall be based upon the quantity of water used in or on the premises as the same is measured by a water or sewer meter or meters. All meters must by acceptable to the City Superintendent. Additional charges for extra strength sewage will be levied where applicable.
The monthly sewage volume charges for residential, educational, religious, public and charitable classifications shall be based on the actual metered water consumption in the months of December, January, February and March. For the months of April through November sewage volume charges shall be based on the average metered water consumption for the months of December through March or the actual metered water consumption for the billing period, whichever is less. Provided, however, that in no case shall the billed consumption in the month of April through November be less than the actual metered water consumption or one thousand gallons, whichever is less.
For residential, educational, religious, public and charitable institution customers establishing a new service for which no metered consumption history exists, the monthly sewage volume for such account is established in accordance with the preceding paragraph.
All such charges as delineated above shall be made in accordance with the schedule of rates set out in Section 15-329 of this chapter.
(Code 1991; Ord. 2000-6, Sec. 3)
Sewer rates and charges shall be as set forth in the city’s fee resolution.
(Ord. 246; Code 1991; Ord. 2000-6, Sec. 4; Code 2010)